FC-ED86 Elevator Linkage Board is mainly used between intercom system and the elevator system which of FCARD series ,it responsible for gather the signal of door and floors which send by intercom system,and transfer the data to the elevator control board ,so that to point out the specified floor to visitors.
FC-ED86 Elevator Linkage Board support the lift main boards FC-8832、MC-5816、FC-2816、FC-2866 and etc, linkage with intercom system, FC-ED86 max support 6 lifts's intercom linkages at same time, support protocol mode and information collection mode.
FC-ED86 support two working modes:
1. linking mode of communication protocol, which is the “expansion board” communicate with the mainframe of building intercom system by RS232 or RS485,and point out the specified floor to visitors by get the instructor.
2. gathering mode of floor signal ,is means that gather the signal of each floor by expansion board and get the visitors to specified floor.If the building intercom system support linking mode,please choose it first,if didn’t support,that you can choose gathering mode.
FC-ED86 support 1 group of USB communication port、1 group of RS232 port which connected with Building Intercom System、1 group of RS485 port which connected with Building Intercom System、 1 group RS485 port that connected to lift access control board、 1 group RS485 port which linkage with elevator expansion board of previous level、6 groups signal input port of elevator to first floor and opened、 8 groups ports used for unlock signal collection.
Humidity: 10 - 90%
Max Floor: 64 floors
Call Lift: 1 group
Operating Voltage：DC9V-14V standard 12V
Operating Current: < 500mA
Operating Temperature: -10℃-75℃ (up to 6 elevators)
Communication Protocol: can be added according to the agreement of different manufacturers
Building Communications: 1 group RS232 interface、1 group RS485 interface
Elevator Communications: 1 group RS485 interface
Main board size: 157mm * 107mm * 18mm
Floor's Collection: 8 groups (max can connect 8 sets of elevator linkage board)
Unlock Signal: 6 groups (can detect the first unlock signal of 6 floor)
Working Mode: Floor collection、floor collection board、protocol linkage mainboard (user defined)
Support lift control: FC-8832、MC-5816 can be added
1. Communication Protocol Mode:
Through Intercom(The building intercom communication port,A connect to A,B connect to B,) or RS232 port connected with the mainframe of building intercom system, to receive the signal send by mainframe.Make the two lines of Elevator call port connect with the call button(is the button on first floor to call the elevator) signal line of first floor to help the guests call the elevator .Make the two lines of ED01 port connect with the detection line which on the elevator door at first floor, in order to let FC-ED86 know the elevator has been down to first floor and opened for guests comes,if there are many elevators that others detection line also can be connect to ED02...ED06 port(Maximum to support 6 elevators working together),if over than six,FC-ED86 expansion line will connect with each other by FRS485,one of the FRS485 port A and B will connect to RS485 of another expansion board(A link to A, B link to B),then put the FRS485 another port A and B of FC-ED86 expansion board connect to the main board A and B (A connect A, B connect to B),lastly,make the FC-ED86 and other device power on.
2. Floors' Signal Gathering Mode:
Make FC-ED86 as the floors’ gathering board(FC-ED86 is set to the certain floor of the gathering board),a board support gather 8 floor signal,so need to add a FC-ED86 board when over than 8 floor,they connected by RS-485 port,maximum to connect 8 boards(To realize gather the signal of 64 floors opened)The floor acquisition board will be connected to the main board through the FRS485 (one of the FC-ED86 is set to the main board mode), Make the two lines of “Elevator call” port connect with the call button(is the button on first floor to call the elevator) signal line of first floor to help the guests call the elevator . Make the two lines of ED01 port connect with the detection line which on the elevator door at first floor,in order to let FC-ED86 know the elevator has been down to first floor and opened for guests comes,if there are many elevators that others detection line also can be connect to ED02...ED06 port(Maximum to support 6 elevators working together),then put the “Intercom” another port A and B of FC-ED86 expansion board connect to the main board A and B (A connect A, B connect to B),lastly,make the FC-ED86 and other device power on.
1. Must be put the Elevator main board installed in the management software completely before the Elevator expansion board used.Then connect the main board information with the expansion board by management software.After all ,the expansion board can be working with the main board.
2. If the building intercom supports RS485 or RS232 to transfer the protocol, you can use the “communication protocol linkage mode” to achieve linkage, and the agreement you can setting by yourself through our management software.
3. Elevator expansion board support called function(Elevator call port),which can be make the Elevator call to first floor,so that convenience to meet the guests.This line must be connected.
4. Elevator expansion board support 6 groups open detection function(ED01-ED06 port),it can connect 6 elevators by ED port,and through ED can detect the elevator has been at first floor,then the elevator can meet the visitors smoothly. Must be connect this line( the switching signal of zero-volt reply).
5. The board is support close delay settings, it is set to make the visitors enter into the elevator smoothly . Please adjust the time according to the distance between the door to the elevator .
6. Use the mode of gather floor signal,each expansion board support gathering 8 floor signal,over than 8 need to add a board,they are working by connected with RS485.Before use it ,please setting the floor parameters that each board need to responsible for.Floor port (Floor 01- Floor 08 port) accept is the Dry node switching signal ( the switching signal of zero-volt replays).
Compatible with FCARD one card management system. Support: Access Control System, Offline Access Control System, Access Control & Time Attendance, Guard Tour, Canteen POS System, Water Controller, Elevator Access Control Board, Parking Lot System etc unified management,to realize one card management system with one card and one database.